Return to Barbeque Grill Articles
Overfilling Prevention Devices For Consumers
This article will provide some background on this new, historic safety
advancement in the use of small propane cylinders...
This information has been developed to create a better understanding relative to the introduction of a new safety device designed to markedly increase the safe use of
small propane cylinders While an occasional inconvenience may occur during the transition to a higher level of propane safety for gas grill tanks, etc., it is the
propane industry's desire that the OPD be recognized by consumers for what it really is... a notable advancement for the safe use of the
Exceptional Energy Propane.
Here then is a listing of answers to consumer's most commonly asked questions. The propane industry hopes that this information will be helpful relative to the
purpose and use of the overfilling prevention device.
What is an overfilling prevention device?
As defined by the National Fire Protection Association's Pamphlet 58 -LP-Gas Code,
1998 Edition (Code), it is...
"A safety device that is designed to provide an automatic means to
prevent the filling of a container in excess of the maximum permitted filling limit."
Typically, the overfilling prevention device will appear as part of a
cylinder valve that is installed as a complete unit into the cylinder. The
cylinder valve will have either a CGA 791 (ACME threads) or a CGA 810
(push-pull, quick disconnect) connection device.
What does the Code require?
A. For propane cylinders in the 4 lb. through 40 lb. propane capacity range,
the Code requires for them to be equipped with an OPD, as follows:
New cylinders for vapor service which are fabricated after September 30,
1998; as cylinders are requalified after September 30, 1998 through March 31,
2002; effective April 1, 2002, before a cylinder is filled.
(All references to "cylinders" applies to only those in the 4 lb.
through 40 lb. propane capacity range. Also, the last page of this document
contains information on the service life and inspection of cylinders.)
How can an OPD be identified when it is installed in a cylinder?
Listed (e. g. Underwriters Laboratories, Inc.) OPD's are easily recognizable by
observing their unique trilobular handwheel. In the
graphic (left), you can see the more traditional propane tank shutoff knob on
the top. Beneath it is the new triangular-shaped handwheel that indicates
the tank has an overflow protection device installed.
The triangular-shaped handwheel is connected
to the valve stem in a tamperproof manner for the purpose reducing the
possibility of putting a user at risk by an attempt to interchange an OPD
handwheel on to a conventional non-OPD valve. It should be noticed that the
valve stem on a non-OPD equipped cylinder is not easily matched with a standard
trilobular handwheel. Those who fill cylinders should take care in observing
whether or not a cylinder that appears to be equipped with an OPD, actually is.
(Note - Prior to the Code's requirement for the use of OPD's, early
non-uniform valves were introduced into the marketplace. Thousands of these
valves had conventional handwheels and were not marked as now required by the UL
listing. While the safety features of these early OPD valves is not being
questioned, those who fill small propane cylinders should be aware of these
valves still being in service. In time, through normal attrition, these first
generation OPD valves will fade from use by attrition.)
Is an OPD intended to be an aid in the filling of a cylinder?
The device is designed to only be a backup in the filling of a cylinder. With
an OPD equipped cylinder, the traditional procedures of filling by the weight or
volumetric methods should be followed.
Is the requirement for OPD's a mercenary ploy by those in the propane
industry to take advantage of consumer's pocketbooks?
This is a good question and deserves a direct answer which is.... no. Those
marketers who fill propane cylinders for customers have had virtually nothing to
do with the advent of the OPD. The term "virtually" is used as there
were a few highly concerned and industry active propane marketers who became
involved in resolving issues which surrounded the advent of OPD's, including a reasonable
time frame for the introduction of these new safety devices into the marketplace.
I have a horizontal cylinder on my recreational vehicle. Are OPD's available
for that kind of service?
The 2001 edition of NFPA 58 (the LP-Gas Code) recognizes that horizontally
oriented cylinders that were manufactured prior to October 1, 1998, are unable
to be retrofitted with the OPD's. As a result of this fact, the Code now exempts
these cylinders from having to be retrofit with OPD valves. Any such cylinder
must have a label affixed to it to inform the user and the refiller that an OPD
valve is not installed.
Why do some propane retail marketers fill cylinders that would normally be
required to be requalified and have an OPD installed, whereas other marketers
require the OPD to be retrofit on the cylinder before they refill it?
Propane marketers of integrity are those that care about the handling and use
of cylinders that they refill, knowing that the families of consumers deserve
the best and safest service that can be offered. If a propane marketer elects to
do otherwise, that choice speaks for itself. Also keep in mind that some states
or jurisdictions have not adopted the 1998 or later editions of NFPA 58.
If the requirement for a cylinder to be equipped with an OPD is not a law in
my state, then how can it be enforced by a propane marketer?
The Code is not adopted, state-by-state, on a uniform basis. In time, most
states, if not all, will move to enforce the OPD criteria which was first
published in the Code's 1998 edition.
What happens if the float breaks off?
If an OPD is determined to inoperable, it should be replaced. For small
portable tanks typically used for gas grills, the cost of replacing the OPD may
be more than the cost of a new OPD-compliant tank!
In another state I recently had a cylinder filled for my deer hunting camp
and they didn't mention anything about an OPD. Are there laws different from
The Code is revised by the National Fire Protection Association every three
years. Virtually all of the individual United States of America have adopted the
Code as their rules for propane applications, but not necessarily on a uniform
basis as to a particular edition. So, as the OPD requirements first appeared in
the 1998 edition of the Code, not all states have updated their propane rules to
that edition. Again, it is expected that all cylinders in the 4 lb. through 40
lb. capacity range will eventually be equipped with an OPD.
Why don't they make one-time-use throw-away grill tanks?
Propane cylinders are manufactured to a comprehensive specification of the U.
S. Department of Transportation. Because of these strict requirements, a
throw-away grill tank service would increase consumer cost to a level that would
be unreasonable and impractical.
Where can I have my tank requalified and a new OPD valve installed? If you
will not requalify my tank, then where can I buy a new one? Where can I dispose
of my old tank?
The propane marketers serving your area should be a reliable source of
information to answer questions regarding the OPD.
Roofers and other commercial customers are trying to use OPD equipped tanks
on torch applications and they are not getting an adequate flow through the
valve. What can we do about this?
Some of the early OPD valves had an insufficient flow capacity for certain
types of service such as high-pressure torch applications. Market competition
has resulted in OPD's becoming available that have significantly greater rates
Propane Cylinders Have A Service Life Which Can Be Extended
According to the U. S. Department of Transportation regulations, small
propane cylinders (e. g. grill cylinders) marketed in the United States, with
normal wear, have a minimum useable life of twelve years from the date of
Each cylinder is required to be clearly marked with specific information that
includes the month and year it was made. Usually, this marking appears on the
protective carry-collar of the cylinder. It may be illegal, either by federal
regulations or administrative code in your states, to refill a small cylinder
that is older than twelve years without being inspected according to strict
procedures. Your local propane marketer should be able to provide you with
information regarding the availability of this service.
This information has been provided to us as a contribution to the safe
use of propane by
National Propane Gas Association and The
Propane Education and Research Council. (5/2002)
Return to Barbeque Grill Articles