Should You Have the Air Ducts in Your Home Cleaned?
Part 1 of 2
Note: This article was authored and researched by the US Environmental Protection Agency. It is a thorough, honest treatment of a home repair procedure fraught with deception and outright fraud by unscrupulous contractors. Do your homework and READ this important article before you invest in duct cleaning. NH
What is Air Duct Cleaning?
Most people are now aware that indoor air pollution is an issue of growing concern and increased visibility. Many companies are marketing products and services intended to improve the quality of your indoor air. You have probably seen an advertisement, received a coupon in the mail, or been approached directly by a company offering to clean your air ducts as a means of improving your home's indoor air quality. These services typically -- but not always -- range in cost from $450 to $1,000 per heating and cooling system, depending on the services offered, the size of the system to be cleaned, system accessibility, climatic region, and level of contamination.
Duct cleaning generally refers to the cleaning of various heating and cooling system components of forced air systems, including the supply and return air ducts and registers, grilles and diffusers, heat exchangers heating and cooling coils, condensate drain pans (drip pans), fan motor and fan housing, and the air handling unit housing (see diagram below.)
If not properly installed, maintained, and operated, these components may become contaminated with particles of dust, pollen or other debris. If moisture is present, the potential for microbiological growth (e.g., mold) is increased and spores from such growth may be released into the home's living space. Some of these contaminants may cause allergic reactions or other symptoms in people if they are exposed to them. If you decide to have your heating and cooling system cleaned, it is important to make sure the service provider agrees to clean all components of the system and is qualified to do so. Failure to clean a component of a contaminated system can result in re-contamination of the entire system, thus negating any potential benefits. Methods of duct cleaning vary, although standards have been established by industry associations concerned with air duct cleaning. Typically, a service provider will use specialized tools to dislodge dirt and other debris in ducts, then vacuum them out with a high-powered vacuum cleaner.
In addition, the service provider may propose applying chemical biocides, designed to kill microbiological contaminants, to the inside of the duct work and to other system components. Some service providers may also suggest applying chemical treatments (sealants or other encapsulants) to seal or cover the inside surfaces of the air ducts and equipment housings because they believe the sealant will control mold growth or prevent the release of dirt particles or fibers from ducts. These practices have yet to be fully researched and you should be fully informed before deciding to permit the use of biocides or sealants in your air ducts. They should only be applied, if at all, after the system has been properly cleaned of all visible dust or debris. [Click on the graphic below for a full page "printable" version.]
Components of a
Residential Heating and
Deciding Whether or Not to Have
Your Air Ducts Cleaned
Knowledge about the potential benefits and possible problems of air duct cleaning is limited. Since conditions in every home are different, it is impossible to generalize about whether or not air duct cleaning in your home would be beneficial.
If no one in your household suffers from allergies or unexplained symptoms or illnesses and if, after a visual inspection of the inside of the ducts, you see no indication that your air ducts are contaminated with large deposits of dust or mold (no musty odor or visible mold growth), having your air ducts cleaned is probably unnecessary. It is normal for the return registers to get dusty as dust-laden air is pulled through the grate. This does not indicate that your air ducts are contaminated with heavy deposits of dust or debris; the registers can be easily vacuumed or removed and cleaned.
On the other hand, if family members are experiencing unusual or unexplained symptoms or illnesses that you think might be related to your home environment, you should discuss the situation with your doctor. EPA has published Indoor Air Quality: An Introduction for Health Professionals that can be obtained free of charge by contacting IAQ INFO at the number listed in this guide. You may obtain another free EPA booklet from IAQ INFO entitled The Inside Story: A Guide to Indoor Air Quality for guidance on identifying possible indoor air quality problems and ways to prevent or fix them.
You may consider having your air ducts cleaned simply because it seems logical that air ducts will get dirty over time and should occasionally be cleaned. While the debate about the value of periodic duct cleaning continues, no evidence suggests that such cleaning would be detrimental, provided that it is done properly.
On the other hand, if a service provider fails to follow proper duct cleaning procedures, duct cleaning can cause indoor air problems. For example, an inadequate vacuum collection system can release more dust, dirt, and other contaminants than if you had left the ducts alone. A careless or inadequately trained service provider can damage your ducts or heating and cooling system, possibly increasing your heating and air conditioning costs or forcing you to undertake difficult and costly repairs or replacements.
You should consider having the air ducts in your home cleaned if:
There is substantial visible mold growth inside hard surface (e.g., sheet metal) ducts or on other components of your heating and cooling system. There are several important points to understand concerning mold detection in heating and cooling systems:
- Many sections of your heating and cooling system may not be accessible for a visible inspection, so ask the service provider to show you any mold they say exists.
- You should be aware that although a substance may look like mold, a positive determination of whether it is mold or not can be made only by an expert and may require laboratory analysis for final confirmation. For about $50, some microbiology laboratories can tell you whether a sample sent to them on a clear strip of sticky household tape is mold or simply a substance that resembles it.
- If you have insulated air ducts and the insulation gets wet or moldy it cannot be effectively cleaned and should be removed and replaced.
- If the conditions causing the mold growth in the first place are not corrected, mold growth will recur.
Ducts are infested with vermin, e.g. (rodents or insects); or
Ducts are clogged with excessive amounts of dust and debris and/or particles are actually released into the home from your supply registers.
Other Important Considerations...
Duct cleaning has never been shown to actually prevent health problems. Neither do studies conclusively demonstrate that particle (e.g., dust) levels in homes increase because of dirty air ducts or go down after cleaning. This is because much of the dirt that may accumulate inside air ducts adheres to duct surfaces and does not necessarily enter the living space. It is important to keep in mind that dirty air ducts are only one of many possible sources of particles that are present in homes. Pollutants that enter the home both from outdoors and indoor activities such as cooking, cleaning, smoking, or just moving around can cause greater exposure to contaminants than dirty air ducts. Moreover, there is no evidence that a light amount of household dust or other particulate matter in air ducts poses any risk to health.
EPA does not recommend that air ducts be cleaned except on an as-needed basis because of the continuing uncertainty about the benefits of duct cleaning under most circumstances. If a service provider or advertiser asserts that EPA recommends routine duct cleaning or makes claims about its health benefits, you should notify EPA by writing to the address listed at the end of this guidance. EPA does, however, recommend that if you have a fuel burning furnace, stove, or fireplace, they be inspected for proper functioning and serviced before each heating season to protect against carbon monoxide poisoning. Some research also suggests that cleaning dirty cooling coils, fans and heat exchangers can improve the efficiency of heating and cooling systems. However, little evidence exists to indicate that simply cleaning the duct system will increase your system's efficiency.
If you think duct cleaning might be a good idea for your home, but you are not sure, talk to a professional. The company that services your heating and cooling system may be a good source of advice. You may also want to contact professional duct cleaning service providers and ask them about the services they provide. Remember, they are trying to sell you a service, so ask questions and insist on complete and knowledgeable answers.
Suggestions for Choosing a Duct Cleaning Service Provider
To find companies that provide duct cleaning services, check your Yellow Pages under "duct cleaning" or contact the National Air Duct Cleaners Association (NADCA) at the address and phone number in the information section located at the end of this guidance. Do not assume that all duct cleaning service providers are equally knowledgeable and responsible. Talk to at least three different service providers and get written estimates before deciding whether to have your ducts cleaned. When the service providers come to your home, ask them to show you the contamination that would justify having your ducts cleaned.
Do not hire duct cleaners who make sweeping claims about the health benefits of duct cleaning -- such claims are unsubstantiated. Do not hire duct cleaners who recommend duct cleaning as a routine part of your heating and cooling system maintenance. You should also be wary of duct cleaners who claim to be certified by EPA. EPA neither establishes duct cleaning standards nor certifies, endorses, or approves duct cleaning companies.
Do not allow the use of chemical biocides or sealants unless you fully understand the pros and the cons (See "Unresolved Issues of Duct Cleaning" in Part 2 of this article).
Check references to be sure other customers were satisfied and did not experience any problems with their heating and cooling system after cleaning.
Contact your county or city office of consumer affairs or local Better Business Bureau to determine if complaints have been lodged against any of the companies you are considering.
Interview potential service providers to ensure:
- they are experienced in duct cleaning and have worked on systems like yours;
- they will use procedures to protect you, your pets, and your home from contamination; and
- they comply with http://www.nadca.com's air duct cleaning standards and, if your ducts are constructed of fiber glass duct board or insulated internally with fiber glass duct liner, with the North American Insulation Manufacturers Association's (NAIMA) recommendations.
Ask the service provider whether they hold any relevant state licenses. As of 1996, the following states require air duct cleaners to hold special licenses: Arizona, Arkansas, California, Florida, Georgia, Michigan and Texas. Other states may require them as well.
If the service provider charges by the hour, request an estimate of the number of hours or days the job will take, and find out whether there will be interruptions in the work. Make sure the duct cleaner you choose will provide a written agreement outlining the total cost and scope of the job before work begins.
What to Expect From an Air Duct Cleaning Service Provider
If you choose to have your ducts cleaned, the service provider should:
Open access ports or doors to allow the entire system to be cleaned and inspected.
Inspect the system before cleaning to be sure that there are no asbestos-containing materials (e.g., insulation, register boots, etc.) in the heating and cooling system. Asbestos-containing materials require specialized procedures and should not be disturbed or removed except by specially trained and equipped contractors.
Use vacuum equipment that exhausts particles outside of the home or use only high-efficiency particle air (HEPA) vacuuming equipment if the vacuum exhausts inside the home.
Protect carpet and household furnishings during cleaning.
Use well-controlled brushing of duct surfaces in conjunction with contact vacuum cleaning to dislodge dust and other particles.
Use only soft-bristled brushes for fiberglass duct board and sheet metal ducts internally lined with fiberglass. (Although flex duct can also be cleaned using soft-bristled brushes, it can be more economical to simply replace accessible flex duct.)
Take care to protect the duct work, including sealing and re-insulating any access holes the service provider may have made or used so they are airtight.
How to Determine if the Duct Cleaner Did A Thorough Job
A thorough visual inspection is the best way to verify the cleanliness of your heating and cooling system. Some service providers use remote photography to document conditions inside ducts. All portions of the system should be visibly clean; you should not be able to detect any debris with the naked eye. Show the Post-Cleaning Consumer Checklist to the service provider before the work begins. After completing the job, ask the service provider to show you each component of your system to verify that the job was performed satisfactorily.
If you answer "No" to any of the questions on the checklist, this may indicate a problem with the job. Ask your service provider to correct any deficiencies until you can answer "yes" to all the questions on the checklist.
Post-Cleaning Consumer Checklist
|General||Did the service provider obtain access to and clean the entire heating and cooling system, including ductwork and all components (drain pans, humidifiers, coils, and fans)?||--||--|
|Has the service provider adequately demonstrated that duct work and plenums are clean? (Plenum is a space in which supply or return air is mixed or moves; can be duct, joist space, attic and crawl spaces, or wall cavity.)||--||--|
|Heating||Is the heat exchanger surface visibly clean?||--||--|
|Are both sides of the cooling coil visibly clean?||--||--|
|If you point a flashlight into the cooling coil, does light shine through the other side? It should if the coil is clean.||--||--|
|Are the coil fins straight and evenly spaced (as opposed to being bent over and smashed together)?||--||--|
|Is the coil drain pan completely clean and draining properly?||--||--|
|Blower||Are the blower blades clean and free of oil and debris?||--||--|
|Is the blower compartment free of visible dust or debris?||--||--|
||Is the return air plenum free of visible dust or debris?||--||--|
|Do filters fit properly and are they the proper efficiency as recommended by HVAC system manufacturer?||--||--|
|Is the supply air plenum (directly downstream of the air handling unit) free of moisture stains and contaminants?||--||--|
|Metal Ducts||Are interior ductwork surfaces free of visible debris? (Select several sites at random in both the return and supply sides of the system.)||--||--|
|Fiber Glass||Is all fiber glass material in good condition (i.e., free of tears and abrasions; well adhered to underlying materials)?||--||--|
|Are newly installed access doors in sheet metal ducts attached with more than just duct tape (e.g., screws, rivets, mastic, etc.)?||--||--|
|With the system running, is air leakage
through access doors or
covers very slight or non-existent?
|Air Vents||Have all registers, grilles, and diffusers been firmly reattached to the walls, floors, and/or ceilings?||--||--|
|Are the registers, grilles, and diffusers visibly clean?||--||--|
|Does the system function properly in both the heating and cooling modes after cleaning?||--||--|